This legislation has been repealed.
(1) Except as
otherwise provided in these regulations, fire hydrants required to be provided
under these regulations shall be in accordance with AS 2419 being item 20 in
Schedule 2 and shall conform to the Building Regulations 1989 made
under the Local Government (Miscellaneous Provisions) Act 1960 .
(2) Where the relevant
Australian Standard so provides fire hydrant installations shall be maintained
in accordance with that standard otherwise a fire hydrant installation shall
be tested at least once in every interval of 12 months in accordance with
the commissioning tests prescribed in AS 2419 being item 20 in
sprinkler fire alarm systems shall be in accordance with AS 2118 being item 21
in Schedule 2.
(4) Any foam
installation shall be in accordance with the relevant parts of section 9
of AS 1940 being item 11 in Schedule 2 or as otherwise approved.
[Part 6 (regulations 6.1-6.25) repealed in Gazette 8 Jun 1999